- GoldenHas donated $ to the upkeep of GPL
Furnace fan stopped blowing last Friday. Called in Centerpoint and they diagnosed the issue as a bad board. They put in a new one, but then our Nest thermostat wouldn’t work. No longer getting power. Guy thought maybe the board he brought was faulty as well, because it was giving him error codes even with his jumper equipment.
They came back today, board this time is fine, but the Nest still wouldn’t work. I have up and agreed to a different thermostat. They hook it up, test all functions, everything works. We could again turn on the heat, fan, and AC from the thermostat they put in.
Then they leave, and the AC won’t come on. Furnace and fan work fine, no AC. Obviously it isn’t needed right now, but I’m still pissed. Time to get on the phone with them for the umpteenth time in the last week.
And people wonder why I have a completely analog 1960s furnace… blower motor separate from furnace (with a rubber v belt no less). I put in a new thermostat to control it (two actually so as to do a crude zonal control but only run one at a time)… but that is as modern as I am going for now … all of it my mechanic and I understand. Super simple. Not the most efficient but not terrible so long as I clean the heat exchanger surfaces occasionally. That and the blower squirrel cage.
Problem is my mechanic is older than me. If he goes before I do I am going to have to train in a new one. Not sure how that’s gonna work.
If you have a mechanic who is trained in on your furnace, my guess is it isn’t as simple as you imply.